|Schedule your inspection today! Call
Exhaust fans should be installed in bathrooms, especially in the tub and shower areas as well as laundry rooms and
are designed to exhaust odors and moist air to the home's exterior. Typical systems consist of a ceiling fan unit
connected to a duct that terminates at the roof.
The fan may be controlled in one of several ways:
- Most are controlled by a conventional wall switch.
- A timer switch may be mounted on the wall.
- A wall-mounted humidistat can be pre-set to turn the fan on and off based on different levels of relative
Ventilation fans should be inspected for dust buildup that can impede airflow. Particles of moisture-laden animal
dander and lint are attracted to the fan because of its static charge. Inspectors should comment on dirty fan covers.
The following conditions indicate insufficient bathroom ventilation:
- Moisture stains on walls or ceilings.
- Corrosion of metal.
- Visible mold on walls or ceilings.
- Peeling paint or wallpaper.
- Frost on windows.
- High levels of humidity.
The most common defect related to bathroom ventilation systems is improper termination of the duct. Vents must
terminate at the home exterior. The most common improper terminations locations are:
- Mid-level in the attic. These are easy to spot.
- Beneath the insulation. You need to remember to look. The duct may terminate beneath the insulation or there
may be no duct installed.
- Beneath attic vents. The duct must terminate at the home exterior, not just beneath it.
Improperly terminated ventilation systems may appear to work fine from inside the bathroom; you have to look in the
attic or on the roof. Sometimes poorly-installed ducts will loosen or become disconnected at joints or connections.
Ducts which leak or terminate in attics can cause problems from condensation. Warm, moist air will condense on cold
attic framing, insulation or other materials. This condition has the potential to cause health or decay problems from
mold, or to damage materials such as drywall. Moisture also reduces the effectiveness of thermal insulation.
Perhaps the most serious consequence of an improper ventilation setup is the potential accumulation of mold in
attics or crawlspaces. Mold may appear as a fuzzy, thread-like, cobwebby fungus, although it can never be identified
with certainty without being lab-tested. Health problems caused by mold are related to high concentrations of spores
in indoor air. “Spores” are like microscopic seeds, released by mold fungi when they reproduce. Every home has
mold. Moisture levels of about 20% in materials will cause mold colonies to grow. Inhaling mold spores can cause
health problems in those with asthma or allergies, and can cause serious or fatal fungal infections in those with lung
disease or compromised immune systems.
Mold is impossible to identify visually and must be tested by a lab in order to be confidently labeled. Inspectors
should refrain from calling anything “mold” but should refer to anything that appears as mold as a material that
“appears to be microbial growth.” Inspectors should include in their report, and in the inspection agreement signed
by the client, a disclaimer clearly stating that the General Home Inspection is an inspection for safety and system
defects, not a mold inspection.
Decay, which is rot, is also caused by fungi. Incipient (early) decay cannot be seen. By the time decay becomes
visible, wood may have lost up to 50% of its strength.
In order to grow, mold fungi require that the following conditions are present:
- Temperatures between approximately 45° F and 85° F;
- Food. This includes a wider variety of materials found in homes; and
If insufficient levels of any of these requirements exist, all mold growth will stop and fungi will go dormant. Most are
difficult to actually kill.
Even though mold growth may take place in the attic, mold spores can be sucked into the living areas of a residence
by low air pressure. Low air pressure is usually created by the expulsion of household air from exhaust fans in
bathrooms, dryers, kitchens and heating equipment.
Ventilation ducts must be made from appropriate materials and oriented effectively in order to ensure that stale air is
Ventilation ducts must:
- Terminate outdoors. Ducts should never terminate within the building envelope.
- Contain a screen or louvered (angled) slats at its termination to prevent bird, rodent and insect entry.
- Be as short and straight as possible and avoid turns. Longer ducts allow more time for vapor to condense and
also force the exhaust fan to work harder.
- Be insulated, especially in cooler climates. Cold ducts will encourage condensation.
- Protrude at least several inches from the roof.
- Be equipped with a roof termination cap that protects the duct from the elements.
- Be installed to manufacturer's recommendations.
The following tips are helpful although not required. Ventilation ducts should:
- Be made from inflexible metal, PVC, or other rigid material. Unlike dryer exhaust vents, they should not droop.
- Have smooth interiors. Ridges will encourage vapor to condense, allowing water to back-flow into the exhaust
fan or leak through joints onto vulnerable surfaces.
Above all else, a bathroom ventilation fan should be connected to a duct capable of venting water vapor and odors
into the outdoors. Mold growth within the bathroom or attic is a clear indication of improper ventilation that must be
corrected in order to avoid structural decay and respiratory health issues.
Bathroom and Laundry Room Exhaust Fans